How To Save Money With Voltage Optimization
The average voltage supply from many national grids around the world is often higher than the ideal operating voltage for most electrical equipment from lighting to motors. For example, a 230V linear appliance used on a 240V supply will take 4.3% more current and will consume almost 9% more electricity than at 230V. As a result, sites fitted with a voltage optimization system often achieve reductions in the region of 5 to 15% for energy consumption, costs, and carbon emissions! To get started in your own voltage optimization application and reduce your energy consumption, the first step is to monitor and identify your present incoming voltage levels. Accsense Electrocorder data loggers are solutions which enable you to determine this for yourself.
With a voltage data logger you can perform:
Data measurement– Identify voltage optimization areas and savings
Ongoing data logging– Capture your voltage profile in detail
Savings Calculations– Determine acceptable voltage reduction
Low-cost Investment– Long-term voltage monitoring provides great ROI
Single Phase voltage monitoring:
Accsense Electrocorder EC-1V
Single Phase voltage and current monitoring:
Accsense Electrocorder EC-2VA
Three Phase voltage monitoring:
Accsense Electrocorder EC-3V
Three Phase voltage and current monitoring:
Accsense Electrocorder EC-7VAR
Effects on Various Electrical Loads
A common misconception about voltage optimization is the assumption that a reduction in voltage will result in an increase in current and that therefore the power consumed will remain constant. While this is true for certain fixed-power loads, most sites actually have a diversity of loads that will benefit to a greater or lesser extent, with energy savings aggregating across a site as a whole. But what about the benefit to the typical equipment at three phase sites?
Three Phase AC Motors
The three-phase induction motor is one of the most common types of three phase loads and is used in many types of equipment including refrigeration, pumps, compressors, fans, conveyor drives and lifting systems. Overvoltage results in flux saturation of the iron core, wasting energy through eddy currents and increased hysteresis losses. The drawing of excessive current results in excess heat output from copper losses. The additional stress of overvoltage on motors will decrease motor lifetime.
However, avoiding overvoltage high enough to cause saturation does not reduce the motor’s running efficiency so you can realize substantial energy savings through reducing iron and copper losses. Motors designed for the nominal voltage should be able to cope with normal variation in voltage within the supply limits (+/-10%) without saturation–these motors are unlikely to be running in saturation, so savings are small.
Reducing voltage to an induction motor will slightly affect the motor speed as slip will increase, but speed is mainly a function of the supply frequency and the number of poles. Motor efficiency is optimum at reasonable load (typically 75%) and at the designed voltage, and will fall off slightly with small variations on either side of this voltage. Larger variations affect efficiency more heavily. Very lightly-loaded motors with loading of around 25% and small motors benefit most from voltage reduction.
Motors driven by Variable Speed Drives will use the same power as before, but may draw more current. It should be noted that with reduced stored energy in the DC Bus capacitors, they may be more vulnerable to power dips.
Switched Mode Power Supplies
Switched mode power supplies will use the same power as before, but will draw a slightly greater current to achieve this, along with slightly increased cable losses and slight risk of the increased current tripping magnetic circuit breakers.
If your lighting loads are in use for a high proportion of the time, you can realize large energy savings on your lighting equipment. After you’ve achieved voltage reduction, incandescent lighting will see a large decrease in power drawn as well as large decrease in light output and an increase in lifetime.
You’ll find that other types of lighting can also benefit from improved power quality, including systems with resistive or reactive ballasts. Fluorescent & discharge lighting is more efficient than incandescent lighting. Fluorescent lighting with conventional magnetic ballasts will see reduced power consumption but also a reduced lumen output from the lamp. Fluorescent lamps on modern electronic ballasts will use approximately the same power and give the same light. To provide the same wattage at the reduced voltage will require a greater current and also increase cable losses. Lighting controllers and ballasts are responsible for generating high levels of harmonic distortion, which can be filtered with some types of voltage optimizers, therefore reducing the need for lighting controllers.
A common concern here is that some lighting will fail to turn on at lower voltages. Usually this shouldn’t be a problem since the aim of voltage optimization is NOT just to reduce the voltage as far as possible, but rather to bring it to the service level voltage at which the equipment is designed to operate most efficiently.
Heaters will consume less power, but give out less heat. Note that thermostatically-controlled space or water heaters will consume less power while running, but will have to run for longer in each hour to produce the required output, resulting in no savings.
Energy and Emission Savings
The energy savings you can achieve by voltage optimization are an aggregation of the improved efficiency of all your equipment across the site in response to the improvements in the power quality problems outlined above. It has been and continues to be a key technique for savings in energy consumption and consequently in carbon dioxide emissions.
Interesting research conducted in Taiwan has suggested that, for an industrial supply with voltage reduction upstream of the transformer, there is a 0.241% decrease of energy consumption when the voltage is decreased by 1%, and an increase of 0.297% when the voltage is increased by 1%. This assumed a mixture of loads including 7% fluorescent lighting, 0.5% incandescent lighting, 12.5% single-phase air conditioners, 5% single phase motors, 22.5% small 3-phase motors, 52.5% large 3-phase motors. It’s likely that a modern installation would have less opportunity, with almost no incandescent lighting, partly high-frequency fluorescent lighting (no savings), some variable speed drives (no savings), and higher motor efficiencies (less waste to save). Other installations may not have the large number of small single phase motors for air conditioning—still the findings are instructive.
You’ll probably find that the best potential for savings can be found with older lighting (incandescent or fluorescent) and discharge lighting with conventional control gear. Therefore older commercial and office premises are likely to have a better saving potential than modern buildings or industrial sites.
In summary, you can realize significant savings by using a datalogger to enact voltage optimization techniques, although as with any product you’re responsible for determining the likely savings in your own environment.
For further information on Accsense Electrocorders, voltage optimization or to find the ideal solution for your application-specific needs, contact a CAS Data Logger Application Specialist at (800) 956-4437 or request more information.
Computer Aided Solutions, LLC. dba CAS DataLoggers is a distributor of data loggers, paperless recorders and data acquisition equipment.
We have the industry’s most complete selection of data logging equipment, with hundreds of different models from more than 18 manufacturers. With data loggers from 1 to 300 channels we can record temperature, humidity, force/strain, pressure, flow, voltage, current, resistance, vibration and other digital signals, in connection with serial (RS-232/RS-485), CAN/OBD or SDI-12 devices. We sell directly to end users and also work through a network of distributors and resellers throughout the United States, Canada, Central and South America.
8437 Mayfield Rd Unit 104
Chesterland, OH 44026
This release was published on openPR.
Permanent link to this press release:
Please set a link in the press area of your homepage to this press release on openPR. openPR disclaims liability for any content contained in this release.
You can edit or delete your press release How To Save Money With Voltage Optimization here
News-ID: 1543703 • Views: 198
More Releases from CAS DataLoggers
Identifying Water Meter Tampering Using a Data Logger
Advanced dataTaker Monitoring Solution Catches Utility Theft CAS DataLoggers supplied the industrial data logging solution for Pasco County Utilities, a provider of utility services to customers at a reasonable cost and in an environmentally responsible manner. The Utility Services Branch provides water and sewer services, reclaimed water, solid waste/resource recovery, recycling, hazardous waste, and street lighting service to most of the residents in Pasco County. The company maintains many remote water
Standalone Data Acquisition System Offers Secure Operation
Record Data Anywhere, Independent of a PC Do you need to record environmental data in the field, away from PC support? Are power outages a concern? At CAS DataLoggers, many of our customers call in requesting a standalone data acquisition system which can simultaneously collect data from two or more different kinds of input sensors. Whether your project involves environmental data collection, industrial process monitoring, or another application, Delphin Expert Series
Wireless Environmental Monitoring for a Tortoise Sanctuary
Temperature and Humidity Data Logger Monitors Habitat CAS DataLoggers is proud to have provided the wireless environmental monitoring solution to Dave Friend, owner of the Ojai Sulcata Project Inc (OSP) in Ojai, California, which rescues and researches the massive Sulcata tortoise. These tough turtles are native to the southern Sahara Desert and are one of the largest species of tortoise on Earth, but their conservation status is currently listed as Threatened:
Accurate Product Quality Testing for Fewer Failures
Delphin Expert Series Provides High-Speed Measurement No matter your manufacturing process, your business can greatly benefit from accurate product quality testing and verification. This way, any failures can be caught as quickly as they are formed. However, the high variability in part formation makes monitoring values such as force and displacement difficult—the difference between a quality and defective part is often measured in milliseconds. Therefore, these demanding applications require a high-speed
More Releases for Accsense
New WiFi Refrigerator Freezer Monitoring Kit from Accsense
Complete Kit for Monitoring Fridge and Freezer Temperatures Do you need a device to monitor the temperature of your perishable products stored in Refrigerators and Freezers? Now Accsense has a wireless kit with everything you need to begin monitoring temperature, right out of the box! This turnkey solution is ideal for hospitals, clinics, warehouses, restaurants and more. New from Accsense, the WiFi Refrigerator/Freezer Monitoring Kit completely automates temperature measurement, alarm notification, and
Accsense Customers Awarded the Gold Seal of Approval
Temperature Monitoring by Joint Commission Standards CAS DataLoggers is proud to celebrate the achievements of our customers! Our world-class Accsense monitoring systems have been in use in America’s hospitals since 2006, providing temperature monitoring, alarming and cloud data storage to protect children’s vaccine supplies, medications, blood products, and lab samples. We work with our customers to aid them in complying with the requirements of their accrediting body, and The Joint Commission
Accsense Electrocorder Offers Discount on Energy Data Loggers
Save 15% off Select Models! Starting today, CAS DataLoggers is offering a 15% discount on select models in its line of Accsense Electrocorder dataloggers! These electrical logging devices monitor power/energy, current/voltage, power factor and more. Our Application Engineers are available with more details—just call 1-800-956-4437! The Accsense Advantage: Accsense Electrocorder products use a constant sampling technique, unlike the single ‘snapshot’ reading of competing devices. When these data loggers start to record, they
Accsense Versalog Releases New Software Version
Versatile 8-Channel Data Loggers for Many Applications CAS DataLoggers is pleased to announce a new software upgrade for Accsense VersaLog dataloggers. Released in July, SiteView 3.1.1 extends functionality while adding various bug fixes. Accsense VersaLog products are ideal to capture and record your crucial data. If you need a cost-effect device to collect data and for local alarming, call CAS DataLoggers today at (800) 956-4437! Powerful Software: SiteView is a PC-based application
Record Current and Voltage with Accsense Electrocorder
DC-3VA Two-Channel DC Voltage and Current Logger Do you need a device to record current and voltage data for machine monitoring, circuitry test, battery charging/discharging, or another application? CAS DataLoggers offers the affordable Accsense Electrocorder DC-3VA Voltage and Current Data Logger Kit which records electrical data on 2 channels at fast sample rates and high accuracy. With its large memory, the DC-3VA is ideal for use in low-voltage and current applications.
Go Wireless with Accsense Monitoring Systems!
Accsense A1-01a Wireless Environmental Monitor CHESTERLAND, OH—May 4, 2016 If you need a device to monitor your product or environment, a wireless system is usually the easiest way to go. Accsense Monitoring systems are commonly used for temperature and humidity monitoring in hospitals and pharmacies, for environmental monitoring in industry and medical cleanrooms, cold chain storage, and in many other industries. Accsense can protect your business from losing inventory, experiencing process